- Perth / Perkins original spare parts
- Perkins repair parts inquiry
- Perkins Parts Service Center
- Perkins Parts System Atlas
- Caterpillar .CAT Diesel Engine Parts
- john deerejohn deere accessories
- Mitsubishi Engine Parts Center
- Genuine Volvo diesel engine parts
- Qianglu Diesel Engine Parts Maintenance Technology
- Perkins Technology Center
- Cummins engine generator parts
- Mitsubishi Diesel Engine Generator Maintenance
- Perkins engine parameters
- Perkins / Perkins industrial engines
- The parameters of the British Willson generator set
- Generator Leasing Service Center
- Volvo diesel generator set
- Diesel generator grid-connected and parallel
- Cummins diesel generator set
- Japan Mitsubishi Diesel Generator Set
- Caterpillar generator set
- Generator dual power conversion cabinet ATS
:0574-26871589 Unit sales : 0574-26871589
:0574-26886646 Accessories Sales : 0574-26886646
:0574-26871569 Maintenance Hotline : 0574-26871569
pass :0574-26892499 True : 0574-26892499
Ground : 宁波戚家山联合路 246-252 号 Address : No. 246-252 , Lianhe Road, Qijiashan , Ningbo
Ningbo Rixin Power Technology Co., Ltd. has the following rental methods for users to choose from:
1. Our company is responsible for the power generation service. We will send a special person to the site to generate electricity for users, and send operating technicians to implement monitoring.
2. Our company provides power generation equipment, is responsible for the installation and operation of power generation equipment, supplies power generation equipment supplies such as cables, parallel cabinets, ATS conversion cabinets, etc. Party A can provide the venue. Ningbo diesel generator rental manufacturer's maintenance method level of generator set, Ningbo diesel generator rental manufacturer's maintenance method level technical support, Ningbo diesel generator rental manufacturer's maintenance method level cost, Ningbo diesel generator rental Manufacturer's maintenance methods level service center, Ningbo diesel generator rental manufacturer's maintenance method level price specification information query, Ningbo diesel generator rental manufacturer's maintenance method level, where is diesel generator rental How much is the maintenance method level of the generator set of the manufacturer? Ningbo Rixin Power Technology Co., Ltd.
Maintenance method level of generator sets of Ningbo diesel generator rental manufacturers
There are four levels of maintenance methods for generator sets:
A-level detailed maintenance method
First, daily maintenance:
1. Check the daily report of the diesel generator set.
2. Check the diesel generator set: oil level, coolant level.
3. Daily inspection of the diesel generator set for damage, leakage, and whether the belt is loose or worn.
Second, weekly maintenance:
1. Repeat the daily A-class diesel generator set inspection.
2. Check the air filter and clean or replace the air filter core.
3. Drain the water or sediment in the fuel tank and fuel filter.
4. Check the water filter.
5. Check the starting battery.
6. Start the diesel generator set and check for any impact.
B-level detailed maintenance method
1. Repeat the daily inspection of A-class diesel generators and weekly inspections of diesel generators.
2. Replace the diesel generator oil. (The oil change interval is 250 hours or one month)
3. Replace the oil filter. (Oil filter element replacement cycle is 250 hours or one month)
4. Replace the fuel filter element. (Replacement cycle is 250 hours or one month)
5. Replace the coolant or check the coolant. (Water filter element replacement cycle is 250-300 hours. Fill the cooling system with supplemental coolant DCA)
6. Clean or replace the air filter. (Air filter replacement cycle is 500-600 hours)
C-level detailed maintenance method
1. Replace the diesel filter, oil filter, water filter, and water and oil in the water tank.
2. Adjust the tension of the fan belt.
3. Check the supercharger.
4. Disassemble, inspect and clean the PT pump and actuator.
5. Remove the cover of the rocker arm, check the T-shaped pressure plate, valve guide and intake and exhaust valves.
6, adjust the nozzle lift; adjust the valve clearance.
7. Check the charging generator.
8. Check the radiator of the water tank and the external radiator of the cleaning water tank.
9. Add water tank treasure to the water tank to clean the inside of the water tank.
10) Check the diesel sensor and connecting wires.
11) Check the diesel instrument box.
D-level detailed maintenance method
1. Replace oil, diesel, bypass, water filter, oil and engine circulating water.
2. Clean or replace the air filter.
3. Remove the rocker chamber cover, check the valve guide and T-shaped pressure plate.
4. Check and adjust the valve clearance.
5. Replace the upper and lower pads of the rocker chamber.
6. Check the fan and bracket, and adjust the belt.
7. Check the supercharger.
8. Check the electrical wiring of the diesel generator set.
9. Check the motor excitation circuit.
10. Check the connection lines in the meter box.
11. Check the water tank and external cleaning.
12. Repair or replace the water pump.
13. Disassemble and inspect the one-cylinder spindle bush and connecting rod bush for wear.
14. Check or adjust the working condition of electronic speed regulation.
15. Inject the lubricating grease at the lubrication point of the diesel generator set.
16. Align the excitation part of the diesel generator with dust removal.
17.Check the axial and radial directions of the turbocharger