- Perth / Perkins original spare parts
- Perkins repair parts inquiry
- Perkins Parts Service Center
- Perkins Parts System Atlas
- Caterpillar .CAT Diesel Engine Parts
- john deerejohn deere accessories
- Mitsubishi Engine Parts Center
- Genuine Volvo diesel engine parts
- Qianglu Diesel Engine Parts Maintenance Technology
- Perkins Technology Center
- Cummins engine generator parts
- Mitsubishi Diesel Engine Generator Maintenance
- Perkins engine parameters
- Perkins / Perkins industrial engines
- The parameters of the British Willson generator set
- Generator Leasing Service Center
- Volvo diesel generator set
- Diesel generator grid-connected and parallel
- Cummins diesel generator set
- Japan Mitsubishi Diesel Generator Set
- Caterpillar generator set
- Generator dual power conversion cabinet ATS
:0574-26871589 Unit sales : 0574-26871589
:0574-26886646 Accessories Sales : 0574-26886646
:0574-26871569 Maintenance Hotline : 0574-26871569
pass :0574-26892499 True : 0574-26892499
Ground : 宁波戚家山联合路 246-252 号 Address : No. 246-252 , Lianhe Road, Qijiashan , Ningbo
Ningbo Rixin Power Technology Co., Ltd. Leasing Service Center has brand new used and reliable diesel generator sets. Before you arrive at the site, follow the strict procedures to maintain the generator set to ensure that you will arrive at your leased site with the most productive and reliable power equipment. Convenient and flexible leasing methods, which can provide you with long-term, short-term and temporary electricity leasing services. There are several types of leasing methods for users to choose from:
1. Our company is responsible for the power generation service. We will send a special person to the site to generate electricity for users, and send operating technicians to implement monitoring.
2. Our company provides power generation equipment, is responsible for the installation and operation of power generation equipment, supplies power generation equipment supplies such as cables, parallel cabinets, ATS conversion cabinets, etc. Party A can provide the venue.
◆ Rixing Power Technology Leasing Service Center provides you with the latest technology and equipment. The diesel generator sets we rent are from well-known brand suppliers, applying the most cutting-edge technology today.
◆ No maintenance costs: Now you can stop having to spend a lot of money on repairs, repair tools and accessories, and you can also get rid of the tiresome maintenance records completely. We do all the work for you. Our lease agreement uniquely covers equipment maintenance, so you no longer have to worry about it.
◆ No storage costs: You don't need to store the equipment yourself. After using the device, just call us and we will send someone to take the device away quickly.
◆ No capital investment required: Leasing does not occupy your commercial capital. You pay only for the equipment you need to complete a specific job. By renting equipment at Rixing Power Technology Leasing Service Center, you can invest the remaining money in other aspects of your business and earn more profits. Keep you away from the cost of owning equipment.
◆ Reduce manpower requirements: Our diesel generator sets are equipped with skilled operators, saving you time and money in training and hiring employees. You also do not need to train your own technicians, as our highly trained technicians will maintain the machinery and maintain their excellent performance.
◆ There is no equipment depreciation problem: It is expensive to purchase diesel generator equipment. The value of generating set equipment will gradually decrease over time. Rixing Power Technology Leasing Service Center allows you to use the latest technology diesel generator set equipment, and also saves you from worrying about expensive depreciation costs. Never again use old equipment to complete the work.
◆ Try before you buy: Maybe you are considering buying a certain generator set equipment and also want to try whether it is suitable for you before buying. Rixing Power Technology Rental Service Center is fully equipped. What could be more suitable than renting a similar machine for trial use with us?
◆ Complement your core needs: Your power needs are always changing, and you also need to keep up with customer needs. Maybe sometimes you don't have the power equipment you need to get the job done, but this is exactly what we have. Trust Rixing Power Technology Leasing Service Center, we will quickly provide you with the power equipment you need to complete your work.
◆ Responsive service: Our technically proficient team can provide you with consultation on the lease and use of diesel generator sets. We will strive to be your trusted leasing company and service provider to make your production easier. Just a call and we'll troubleshoot for you.
Diesel generator set rental has the following models: users can choose the corresponding power according to their actual load conditions
ECM for generator rental prices in Cixi area — no communication fault diagnosis tree, ECM for generator rental prices in Cixi area — Technical support for no communication fault diagnosis tree, ECM for generator rental prices in Cixi area — no communication fault diagnosis tree cost, Cixi area ECM for generator rental price — Non-Communication Fault Diagnosis Tree Service Center, ECM for Cixi Area Generator Rental Price — Non-Communication Diagnosis Tree Price Specification Information Inquiry, Cixi Area Generator Rental Price ECM — No Communication Failure Diagnosis Tree , ECM of Cixi area generator rental price — how much is the non-communication fault diagnosis tree, Cixi area of generator rental price ECM — no communication fault diagnosis tree, Ningbo Rixin Power Technology Co., Ltd.
ECM — No Communication Troubleshooting Tree Symptom No Communication, but Cummins ISX15 CM2250 SN Diesel Engine Can Start Without Communication No Cummins ISX15 CM2250 SN Diesel Engine Can Start Without Communication Related to INSITE ™ Service Software Error Communicate with Some ECM but Not All ECMs on the multi-module Cummins ISX15 CM2250 SN diesel engine.
How to use the diagnostic tree This troubleshooting step can be used to diagnose communication problems with the J1939 and J1587 data communication interfaces between the service software and the ECM. Supporting this troubleshooting tree may require 4 steps:
Steps 022-999 (Service Software and Hardware-Overview) in Section F of the corresponding Electronic Control System Troubleshooting and Troubleshooting Manual.
Steps 019-165 (SAE J1939 Data Communication Interface Circuit) in Section 19 of the corresponding Electronic Control System Troubleshooting and Troubleshooting Manual.
Steps 019-166 (SAE J1587 Data Communication Interface Circuit) in Section 19 of the corresponding Electronic Control System Troubleshooting and Troubleshooting Manual.
The troubleshooting steps in this step were created based on the information in the previous step. The troubleshooting steps must be performed in the order specified in the troubleshooting steps.
This troubleshooting step supports several series of Cummins ISX15 CM2250 SN diesel engines, so some instructions are stated in a conventional manner. The required steps and measures apply to a specific Cummins ISX15 CM2250 SN diesel engine series according to the specific Cummins ISX15 CM2250 SN diesel engine series. These documents can be found in the specific Cummins ISX15 CM2250 SN diesel engine series fault judgment and troubleshooting manual.
Overhaul Tips There are three basic principles that must be followed when defining and sequencing the troubleshooting steps listed in this fault tree.
Verify the operation of the high-level system before troubleshooting individual components of the system. The purpose of this is to understand the working behavior of the system so as to guide to the next step of troubleshooting.
Separate the ECM from the vehicle using a baseline ceiling harness to isolate the ECM from vehicle problems that may cause no communication.
Before troubleshooting a single part of the system, a second vehicle or a second ECM should be used to isolate high-level system problems.
Troubleshooting and troubleshooting steps
Step Technical Specifications
Step 1. INSITE ™ Service Software Error Code Check
Step 1A. Check for INSITE ™ service software error code 5023. Is there an INSITE ™ service software error code 5023?
Step 1B. INSITE ™ Service Software Error Code 5080 or 5081 Check. Is there an INSITE ™ service software error code 5080 or 5081?
Step 1C. INSITE ™ Service Software Other Error Code Check. Are there any INSITE ™ service software error codes other than 5023, 5080, or 5081?
Step 1D. ECM Password Check Does the INSITE ™ service software indicate that ECM is password protected?
Step 2. Initial check of data communication interface adapter and INSITE ™ service software
Step 2A. Initial data communication interface adapter check Is the communication indicator on the data communication interface adapter blinking?
Step 2B. Data communication interface adapter reset check ECM is communicating?
Step 2C. INSITE ™ Service Software Initialization Check Does ECM communicate?
Step 2D. Data Communication Interface Adapter Confirmation Check Are you using Inline or Inline I to communicate with the ECM?
Step 2E. Data communication interface adapter firmware check Is the firmware version compatible with the ECM?
Step 3. Checking the reference communication settings
Step 3A. Baseline setting availability check Is the baseline setting available?
Step 3A-1. Cummins ISX15 CM2250 SN diesel engine startup check
Step 3B. Initial baseline communication check Is ECM using baseline communication?
Step 3B-1. Cummins ISX15 CM2250 SN diesel engine startup check
Step 3C. 2nd car or 2nd ECM availability check for baseline setting Is the 2nd car or 2nd ECM connected to the baseline setting?
Step 3D. Initial benchmarking functionality check Does the second ECM use benchmarking communication?
Step 3E. Troubleshoot the benchmark setting Is the benchmark setting check good?
Step 3F. Data Communication Interface Adapter Replacement Check Does the baseline setup use the replacement data communication interface adapter to communicate with the second ECM?
Step 4. ECM power-up circuit check
Step 4A. Cummins ISX15 CM2250 SN diesel engine configuration check Is the Cummins ISX15 CM2250 SN diesel engine equipped with a shut-off valve?
Step 4A-1. Check the voltage of the fuel shutoff valve
Step 4A-2. Coolant temperature sensor signal voltage check
Step 4B. ECM key switch check Is the key switch voltage within the vehicle system voltage 1 VDC?
Step 4C. Check ECM power and ground. Is the ECM battery supply voltage equal to the battery voltage?
Step 5. Initial service software check
Step 5A. Benchmark settings previously used for troubleshooting checks In the check in step 3, did you successfully communicate with the ECM using the baseline settings?
Step 5B. Service software availability check for the second car Can the second car connect to the service software?
Step 5C. Initial service software functionality check Does the second ECM use the service software to communicate with the ECM?
Step 6. Data communication interface adapter power check
Step 6A. Data Communication Interface Adapter Confirmation Check Is the Inline I data communication interface adapter being used to communicate with the INSITE ™ service software?
Step 6B. Check the power of the data communication interface adapter Is the power indicator of the data communication interface adapter on?
Step 6C. Determine if communication is attempted on the OEM meter connector. Is communication attempted on the OEM data communication interface meter connector?
Step 6D. OEM data communication interface meter connector voltage check Is the voltage equal to or greater than 9 VDC?
Step 6E. Check the voltage of the auxiliary power of the data communication interface adapter Is the voltage equal to or greater than 9 VDC?
Step 6F. Check vehicle battery voltage Is the voltage equal to or greater than 11 VDC?
Step 6G. Computer serial port voltage check Is there a minimum 5 VDC voltage?
Step 7. Data communication interface circuit check
Step 7A. Check J1939 or J1587 circuit. Is the circuit check good?
Step 8. Initial service software check
Step 8A. Service software availability check for the second car Can the second car connect to the service software?
Step 8B. Initial Service Software Functionality Check Does the 2nd ECM use service software to communicate?
Step 9. Detailed service software check
Step 9A. Troubleshooting service software hardware Is the service software hardware check normal?
Step 10. Serial cable and computer check
Step 10A. Troubleshooting serial cable and computer Is the serial cable and computer checked properly?
Step 11. ROM starts ECM
Step 11A. ROM boot tool availability check Is the ROM boot tool available?
Step 11B. Does the ROM initiate ECM ECM communication? How much does Ningbo diesel generator lease, how much is Haishu diesel generator lease, how much is Jiangbei diesel generator lease, Ningbo lease generator, Jiangdong lease generator, Haishu lease generator, Zhejiang lease generator, Ningbo generator lease, Xiangshan Leased generator, Luzhou leased generator, Ninghai leased generator, Jiangbei leased generator, Zhenhai leased generator, Beilun leased generator, Dinghai leased generator, Zhoushan leased generator, Yuyao leased generator, Fenghua leased generator, Cixi Rental generator, rental generator, Shengsi rental generator, Jiangdong generator rental, Sheshan rental generator, Putuo rental generator, Jiangbei generator rental price, how much Jiangdong generator rental price, Haishu generator rental price How much is the price of Ninghai generator rental, which place has generator rental